SUMMARY: Water Softener Plant
1. Softener Ion-Exchange Resin Vessel (FRP) (Size 10×54″) 1 No’s.
2. Manual Control Valve for Silica Sand & Resin. 2 No’s.
3. Fitting UPVC S/40 1 Job.
4.Brine Tank 80 Liter
Softener Filter Ion-Exchange Resin
Function (The process ion-Exchange Occurs Through the resin beads. The Negative Charged
Molecules, Calcium & Magnesium are attracted to the positive bound of the resin.)
Quantity 01 No
Flow Rate 900 LPH
Pressure Drop 3 to 4 psi
Min Working Pressure Bar 1.3
Max Working Bar 8.5
Test Pressure Bar 10.5
Max Working Temp 50 C
Size of Vessel (150PCI 10″x 54” )Material of Vessel FRP (Fiber Reinforced Plastic)
Inlet & Outlet Size 1″ Softener Media Ion-Exchange Resin
Media Resin Food Grade 25 Ltr
Manual Softener Valve
Softener control valve is been used to control back wash & REGARNATION
cycle for the Media filters & to keep water treatment system working at maximum
performance at 24 hour. per the raw water quality & usage of water.
FITTING & INSTALLATION MATIRIAL : Fitting Material UPVC S/40.